Sigma CP sounder controller datasheet
The board provides 8 additional sounder outputs which can be configured as zoned, 2-stage or common alarm.
All sounder outputs are open and short circuit monitored and any faults on the sounder outputs will be announced at the main fire alarm panel as a sounder fault.
A class change input is provided which, when activated by a volt free contact closing, will switch all sounder outputs on.
Up to 7 Sounder boards can be connected to a control panel and each is allocated an address from 1 to 7 using a binary coded DIL switch. Sounder boards may be connected to the Sigma CP serial bus in addition to Sigma CP ancillary boards and Sigma CP-R repeater panels.
The total length of the data cable from the main panel to the last repeater must not exceed 1200 metres.
Click on the icons to download the documentation
Get in touch