Sigma CP-R datasheet
Repeaters are available with 2, 4 or 8 zones and in mains powered (K versions) or 24V powered (E versions).
Mains powered repeaters require only a two core data cable from the main control panel. 24V DC versions require an additional two cores for power either from the main panel or from another 24V DC source.
A mixture of Repeaters or Ancillary boards up to a maximum of 7 of each type can be connected to a control panel and each is allocated an address from 1 to 7 using a binary coded DIL switch. The total length of the data cable from the main panel to the last repeater must not exceed 1200 metres.